Installation instructions for polishing and dust removal and maintenance of the unit
Installation instructions for polishing and dust removal
Before installation, check the integrity of the unit and re-tighten the connecting bolts.
The installation position should pay attention to the inspection door is easy to open, the overflow box and water supply pipeline are easy to observe and operate.
The installation of the unit must be level.
The drain water pipe and overflow box should not be directly connected to the water pipe, but should be connected to the water tank or the funnel and then to the sewage pipe to observe the working condition of the unit at any time.
Grinding, polishing and dust removal unit maintenance
When the dust removal system is working, the air volume passing through the unit should always be kept within a certain range, and the fluctuation of air volume should be minimized.
Always pay attention to the tightness of the sight hole, observation hole and each inspection door.
According to the operating experience of the unit, periodically flush the dust inside the unit and on the automatic control electrodes.
If the blade is damaged due to wear or corrosion, it must be repaired or replaced in time.
When passing the dust-containing gas, it is not allowed to operate under the condition of insufficient water level, let alone without water.
The water level automatic control device should be kept clean to prevent dust from entering the operation box, and it should be repaired in time when it is found that the automatic control system fails.
When high and low water levels occur, the cause should be identified in time to troubleshoot.
When the bottom of the overflow box is found to be clogged, you can open the tube cap at the bottom of the overflow box and connect the 1/2 stop valve to the pressure water for cleaning.