|Industrial dust treatment equipment series|
|Welding fume exhaust gas treatment series|
|Grinding polishing dust removal equipment|
|Stand-alone dust collector|
|Spiral duct and accessories series|
1. Air volume calculation and selection:
According to the size of the hood, calculate the exhaust air volume of the fan, the corresponding air volume of the industrial dust treatment , determine the total treated air volume according to the amount of industrial dust and the installation position, and select the specifications and models of the corresponding dust collectors.
、选择相匹配的风机风量，风机的风量选择一般与净化器的处理风量相当，（此数据仅供参考，具体由工程商按现场情况而定，如果风机的风量选择过大于净化器的最大处理风量时会影响净化器的净化效果）。 2. Select the matching fan air volume. The fan air volume selection is generally equivalent to the processing air volume of the purifier. (This data is for reference only. It depends on the actual conditions of the project. If the air volume of the fan is too large than the maximum of the purifier, When processing the air volume, it will affect the purification effect of the purifier). Under the condition that the air volume of the fan meets the requirements of the exhaust air, the smaller the air volume of the fan, the better the effect of the purifier, and the wind speed passing through the purifier is preferably the lowest.
、 工业除尘器的安装与烟罩出口位置的距离至少合适，以确保消防安全和工业净化效果；工业吸尘器与风机的距离也要合适，净化器装在风机的前面，如果风机需要安装在净化器的前面，风机的出风口不能对着净化器直吹，否则会影响净化器净化效果；净化器的进风口最好不能有弯头比较好。 3. The distance between the installation of the industrial dust collector and the outlet of the fume hood is at least appropriate to ensure the fire safety and industrial purification effect; the distance between the industrial vacuum cleaner and the fan should also be appropriate. The purifier is installed in front of the fan. If the fan needs to be installed in the purification In front of the air purifier, the air outlet of the fan must not be directed at the purifier, otherwise it will affect the purifying effect of the purifier; it is better that the air inlet of the purifier does not have an elbow.
度以上直角自由开启空间以便于日后保养、清洗、维修。 4, industrial vacuum equipment can be installed indoors and outdoors, outdoor installation of the purifier, please install a rainproof device above the machine to increase the service life of the machine, maintenance space needs to be reserved around the purifier, the cabinet door should have a right angle of 90 degrees or more Open space for future maintenance, cleaning, and repair.
、机器在安装前最好先通电试行一段时间，检验机器的电极是否会在运输或搬运中产生偏移。 5 , it is best to test the machine for a period of time before installation to check whether the electrodes of the machine will shift during transportation or handling.
、机器的进出风口可以随意互换，进风口方向必须要有过滤网。 6. The air inlet and outlet of the machine can be interchanged at will, and a filter must be installed in the direction of the air inlet.
、设备箱体必须安全接地。 7. The equipment cabinet must be safely grounded.
、接好排风管（注意：绝对不能堵住排出口）。 8. Connect the exhaust pipe (note: the exhaust port must not be blocked).
、净化器通过法兰与排风风管连接，所有连接应密封、防止漏风，漏油的情况。 9. The purifier is connected to the exhaust air duct through the flange. All connections should be sealed to prevent air leakage and oil leakage.
、确保安全，工业除尘器要求能与风机联动，即净化器跟风机同时开同时关；如不能联动的，应做到在启动净化器之前必须先启动风机运作，关机时应先关掉工业吸尘设备后再停风机。 10. To ensure safety, the industrial dust collector needs to be able to interact with the fan, that is, the purifier is turned on and off at the same time; if it cannot be linked, the fan must be started before the purifier is started, and the industrial should be turned off when the machine is shut down. Stop the fan after the vacuum equipment.