|Industrial dust treatment equipment series|
|Welding fume exhaust gas treatment series|
|Grinding polishing dust removal equipment|
|Stand-alone dust collector|
|Spiral duct and accessories series|
How are the equipment and piping of the dust collector equipment factory arranged? We can learn from the following points:
． 1 . 的布局 Layout of dust collector equipment
① The layout of the dust collector equipment is related to the manufacturing design and the layout of the workshop. We often bring the dust collector equipment and related parts close to the advanced technology. This improperly occupies less equipment in the layout, and can also shorten the length of the duct and save costs. However, in some special cases, it is When the air volume is very large, the dust removal equipment and fan must be installed away from the dust.
② In general, when many kinds of dust appear, we can use many independent systems for distributed arrangement, and also can combine many dust points to form a central dust removal system.
台风机 运作时可设有调节风阀，用1 台风机 输送多台设备粉尘源点的烟气时，应调置风阀开关门，让每个系统之间保持平衡正常运作。 ③ In order to prevent the systems from being connected to each other in series, each source of dust is equipped with a damper when operating a fan . When a fan is used to transport the smoke from multiple sources of dust, the damper should be adjusted. Open and close the door to keep the normal operation between each system.
④ In order to make the flue gas distribution uniform and easy to operate, the system of the dust removal equipment should be symmetrically configured.
⑤ When configuring the dust collector equipment, fully consider the requirements required during installation, construction, maintenance and operation, and free up the operating site and transportation passage for the installation vehicles required by the construction machinery.
⑥ For the operation of smelting boilers, a bypass flue and a bleed valve should be considered before the flue gas enters the dust removal equipment system, so that when we open the furnace, the gas that cannot enter the dust removal system or the flue gas in the event of an accident occurs.
． 2 . 器设备厂除尘管道的布局 The layout of the dust removal pipe of the dust collector equipment factory
除尘器设备 烟气输入管道布局前应在保证粉尘的源点可以正常的排烟但不妨碍运作和维修的情况下，风管内不积灰或少量积灰，方便于维修，且风管路线布置最短。 ① Before the layout of the flue gas input pipe of the dust collector equipment, the dust source can be discharged normally without affecting the operation and maintenance, and there is no ash accumulation or a small amount of ash accumulation in the duct, which is convenient for maintenance and the duct route The shortest layout.
于 6米，穿插公路时管底离道路路面的高度不能少 于 5米。 ② When the flue gas duct of the dust collector passes through the railway, the height of the bottom of the pipe and the railway track should not be less than 6 meters, and the height of the bottom of the pipe from the road surface should not be less than 5 meters.
大于 45 °， 在下面装置集中灰斗。 ③ The dust from the outlet of the dust source to the mouth of the dust removal equipment has a large magnetic quantity and large dust particles in the flue gas. The pipeline should be arranged in a slope with an angle of slope greater than 45 °. A centralized ash hopper is installed below.
④ The flue gas duct of the dust collector should be sealed. Except when the pipes to be disassembled are connected by flanges, the other ground directions should be connected by welding. 用 3-5MM的密封胶条。 In order to ensure the tightness of the flange connection, 3-5MM sealing tape should be used .
⑤ Dust removal equipment factory should be installed from the top or surface of the supervisor during the installation of the main pipeline butt connection process.