|Industrial dust treatment equipment series|
|Welding fume exhaust gas treatment series|
|Grinding polishing dust removal equipment|
|Stand-alone dust collector|
|Spiral duct and accessories series|
Electrostatic dedusting equipment is an indispensable auxiliary equipment for thermal power plants. Its role is to remove particulate smoke from the flue gas emitted from the furnace or oil-fired boiler, thereby greatly reducing the amount of flue gas emitted to the atmosphere. This is to improve environmental pollution and Important environmental protection equipment for air quality. Electrostatic dedusting equipment in thermal power plants has high purification efficiency, low resistance loss, high temperature resistance, large flue gas treatment capacity, and low operating costs. It is widely used in power, metallurgy, steel, chemical, building materials and other industries. Compared with other types of dust removal equipment, the present invention uses the lowest energy to separate dust particles, which has the characteristics of high dust removal efficiency, small daily maintenance workload, and low operating cost.
Electrostatic dust removal equipment for thermal power plants It is divided into two parts: the structure of the electrostatic precipitator includes the anode system, the cathode system, the cathode and anode system vibration devices, the incubator, the uniform gas distribution device, the casing, the ash bucket and the ash discharge conveying device, etc. The main body and the high-voltage power supply device Including the dust collection tank and corona discharge electrode system in the main body, discharge electrode vibration and transmission, incubator, ash bucket, ash discharge device, hot air purification system, access to and from the flue, chimney, housing, etc. In addition to the cathode using a small frame The top vibration is also used to reduce the shear force of the cathode line and avoid disconnection. The high-voltage power supply device includes outdoor-side outlet bushing high-voltage rectifier transformers, control cabinets, and high-voltage isolation switch boxes.
Electrostatic dust removal equipment for thermal power plants Its working principle is to use a high-voltage electrostatic field to separate dust from the dust-containing gas. When the power to the corona wire reaches a sufficiently high voltage, a corona zone is generated around the corona wire. Gas ionization generates a large number of free electrons and positive ions. When a dust-containing gas passes through a space containing a large number of electrons and positive and negative ions, the ions and electrons will adhere to the dust and move in the opposite polarity direction, thus causing positive electrode and corona. Positive and negative electricity is released on the wire and adheres to the dust. Vibration dust removal falls into the ash hopper and the dust removal equipment discharges.
Related recommendation: Introduction of electrostatic precipitator
More electrostatic dust removal equipment for thermal power plants 致电400-622-6298！ , Working principle, price, design scheme, welcome Yuchen dust removal equipment manufacturers to call 400-622-6298!